ULC is pleased to announce the publication of the Fifth Edition of CAN/ULC- S, Standard for. Inspection and Testing of Fire Alarm Systems. This National. Fire Alarm Inspection, Maintenance, and Service by Anubis Systems Technologies. SCOPE. This Standard provides requirements for the inspection and testing of fire alarm systems and specifies the devices and functions to be inspected.
|Published (Last):||23 June 2011|
|PDF File Size:||15.64 Mb|
|ePub File Size:||1.55 Mb|
|Price:||Free* [*Free Regsitration Required]|
The montly test is to ensure that all audible and visual alarm indicators function properly and are loud or visible enough to alert all the occupants to a fire condition. This type of detector is best used in residential applications, as it provides extremely good early warning to smoldering type fires that tend give off dense smoke and noxious fumes.
CAN/ULC-S Fire Alarm Annual Inspection Test Form
Abnormally frequent false tripping of dry-pipe valves? Catholic Umbrella Pool II. Check concentration of antifreeze? Is the building fully sprinklered? The pump manufacturer may specify additional testing requirements.
Correct designations for common control functions and indicators.
CAN/ULC-S | Standards Council of Canada – Conseil canadien des normes
Dry-pipe full flow trip test to be done every 3rd year: Valve supervisory switches indicate movement? Low temperature supervisory device tested. Description Type Model No.
Direct Connection yes no Number of Conventional Zones: Standard sprinklers less than 50 yrs old. Record the date, revision and version of firmware: Monthly Testing – Requires the building management or designated individual to actually initiate a fire alarm by activating one x536 the building’s pull stations.
Main drain test shall be conducted on each system riser. For detectors that cannot be properly tested, your local authority may require you to initiate a replacement program where a certain number of detectors are upgraded automatically every year.
Refer to Appendix F2 ; iv A battery capacity meter test. Most house fires start in the electrical wiring so it’s a good idea to have a battery operated smoke alarm installed as a “back-up”. Low temperature alarms in dry pipe, pre-action and deluge valve enclosure passed test?
The communicator has been reset following completion of testing. Termination points for wiring to field devices secure. Beam type smoke detectors inspected and tested.
It might be a good idea to suggest that they practice their individual escape plans during the test as well. Trouble signal silence switch operates.
Standards Council of Canada
cqn Photoelectric type smoke detectors utilize an infrared light source called the emitter and a receiver, both of which are located inside the sensing chamber. Testing Items Quarterly Water flow alarms passed test and provide correct annunciation? Tests to be done every fifth year: Actual number of End-of-Line Resistors tested: Vancouver, Richmond, and Langleythe individuals performing annual testing must be registered by ASTTBC or certified by an agency recognized by the e536 authority.
Jockey pump operational and in good condition? Record anti-freeze Specific Gravity: Sprinklers shall be inspected from floor level?
For homeowners with ten year old multi-station type smoke alarms or who may be contemplating changing or upgrading their existing units! Actual Time to Test Building: